Q
Problem solve Get help with specific problems with your technologies, process and projects.

Consolidating to high density blade servers can be a big step towards streamlining your data center. But data center managers need to research how to cool these servers. Bob Macfarlane explains.

We're consolidating our servers. We've got a bunch of Wintel servers currently. We have a good sense of what doing so will mean in terms of management, but we were looking at consolidating some workloads onto blades. We were warned about heating and cooling issues. I thought consolidating would reduce my heating loads - you know, fewer servers, less heat. Is this not the case?

The problem you're hearing about results from heat density, not from total heat. Blades may reduce total power consumption by as much as 20% over discreet servers, assuming equivalent quantities and processing capabilities, but that remaining 80% or more is packed into a much smaller space. For example, instead of 2,000 Watts per cabinet spread over let's say ten cabinets, you might now have 16,000 Watts in just one cabinet. Watts per Square Foot (W/sf) has become a rather meaningless number but, for comparison's sake, this amounts to nearly 2,000 W/sf in a cabinet 28" Wide x 42" Deep, as opposed to about 333 W/sf for your present servers in smaller cabinets. (Don't try to mount high-density devices in small cabinets. The cable will block whatever air you have.)

It would take nearly 3,000 CFM (Cubic Feet per Minute) of 55 degree Fahrenheit air to handle this kind of heat density, assuming your air conditioners are set for 72 degree Fahrenheit Return Air. This is impossible to accomplish with under-floor air alone. Even if you could do it, you'd have air moving over 17 MPH through two standard tiles in front of a cabinet, and you wouldn't get the air evenly distributed all the way to the top of each cabinet. Using "Grate Tiles" brings it down to 8 MPH, but that's still way too high and you'd probably starve other parts of your data center for air in the process. Even increasing aisle widths doesn't do it. There are really only three ways to solve the problem:

1. Put only one Blade Chassis in a cabinet and spread them out so the load is distributed across a larger part of the data center. This is what most people are doing these days. It doesn't help much with space, but it keeps these expensive servers from going into thermal shutdown.
2. Install "Spot Cooling", such is available from Liebert ("XD" System), or install a High Density Room within the data center such from APC ("InfraStruXure High Density with Integrated Cooling").
3. Install Liquid-cooled Cabinets such as the Knurr "Cyberchill", the Rittal "Liquid Cooling", or the Sanmina "EcoBay". (Yes, sooner or later, you WILL have water piping back in your data center!!).

Whatever you do, make sure to close all unused panel spaces and openings to keep hot air (rear of cabinets) from re-circulating back to the front of the cabinets and reducing the effectiveness of the cold air entering the servers. This is known as "Bypass Air" and is one of the worst enemies of effective cooling. And, of course, make sure those cables don't block the air paths.

Cooling these devices can get tricky, but it's the way technology is moving so don't shy away from it. Just learn to handle it, but that may take expert assistance.

Have a question for an expert?

Get answers from a TechTarget expert on whatever's puzzling you.

You will be able to add details on the next page.

Start the conversation

Send me notifications when other members comment.

SearchWindowsServer

• Battle lines over Windows Server 2008 migration drawn

Microsoft and AWS stepped up their ongoing battle promoting a variety of Windows Server 2008 migration tools in hopes of luring ...

• Build a PowerShell logging function for troubleshooting

A basic administrative skill is checking over logs to find out why something broke. Learn how to build a proper logging mechanism...

• January Patch Tuesday fixes cryptography bug found by NSA

The U.S. National Security Agency shared information with Microsoft about a significant spoofing vulnerability in Windows that ...

SearchServerVirtualization

• Use multiple Dockerfiles for complex application configuration

Dockerfiles can help with application configurations, but there are some questions you must consider, such as how many ...

• An introduction to VMware vRealize Operations Cloud

VMware is set to release a cloud-based management software as a service in 2020, which uses predictive analytics and AI features ...

• Compare vCenter Foundation vs. Standard before implementing

VMware's vCenter software comes in two different versions: Foundation and Standard. Both enable SMBs to create hosts and VMs, but...

SearchCloudComputing

• AWS multi-account management best practices with Control Tower

With the help of AWS Control Tower, organizations who own and operate multiple cloud accounts can manage them all under one roof ...

• Beat vendor lock-in with a cloud exit strategy

Without a comprehensive cloud exit strategy, an organization might fall victim to vendor lock-in and find itself dependent on ...

Google Cloud has rolled out a new Premium Support offering aimed at deep-pocketed enterprises with larger, more complex ...

Close