In a cabinet scenario, you should run your power to one side and your data cabling to another. Another scenario is to run your power in the back and data cabling in the front. Most cabinet manufacturers supply channels for the cabling, others supply just openings, but the main point is to provide as much separation as possible.
In a rack situation, it is a bit easier because you have wire managers to assist with the routing of your data cables. You should have one 10" minimum vertical and one horizontal manager per patch panel. I hope this answers your question.
Should you need more information, or have any other questions, feel free to ask. If you are looking at a particular cabinet or piece of equipment, I will be happy to help with an individual scenario as well.
Dig Deeper on SDN and other network strategies
Related Q&A from Carrie Higbie Goetz
A few factors can indicate it's time to replace a business phone system. Learn when it may be time to switch and how to decide on a course of action. Continue Reading
Migrating UC to the cloud doesn't mean leaving your SIP trunk carrier behind. Learn how bringing your own SIP to cloud services can benefit your ... Continue Reading
An unguarded VoIP system could be vulnerable to attack. Learn what security measures can help prevent VoIP security threats from affecting your ... Continue Reading
Have a question for an expert?
Please add a title for your question
Get answers from a TechTarget expert on whatever's puzzling you.