Q
Problem solve Get help with specific problems with your technologies, process and projects.

# Obtaining reasonably accurate numbers for actual power consumption is difficult enough

## A reader questioned our expert on one of his responses. See how he defended himself.

After reading your article " Cooling Blade Servers" from 21 July 2005, I wondered why you use the power supply Watt rating instead of something like a Rejected Air Heat (BTU) or a percent efficiency rating to feed the formula? Using the power supply Watt rating in the formula seems to say that the unit is 100% inefficient. Also, I cannot find information relating to the 1.08 term (in the equations).
Read the original article on data center cooling: Cooling blade servers.

The fact is, computing hardware is so close to 100% inefficient that converting actual power in Watts directly...

to heat (at 3.4 SBTU per Watt) is extremely close to reality. And since the actual theoretical conversion is 3.412 SBTU per Watt, a small amount of "unconverted power" might be considered to have already been taken into account by using the more commonly used 3.4 conversion factor.

The first law of thermodynamics, known as conservation of energy, states that energy can neither be created nor destroyed – it can only change from one state to another. Incoming electric power is electromagnetic energy. The Ethernet or optical fiber output from a server or data switch is also of electromagnetic form, but the amount of actual energy in those signals is so miniscule compared with the electrical input to the compute device as to be negligible. If the device contains disk drives, there will also be some electrical power converted to mechanical kinetic energy in the spinning discs. But, again, the amount of mechanical energy is so small compared with the heat produced in the process of overcoming the inertia of the discs and maintaining their velocities at the very high rotational speeds at which they operate, that it is simply not worth taking into account in making practical computations of the kind we are discussing. Further, outside of a sophisticated laboratory, we have no realistic way of measuring the amount of power that is converted to something other than heat (or, conversely, to measure both the incoming power and the heat release with such accuracy as to be able to calculate the conversion differential).

If a manufacturer follows ASHRAE's recommended guidelines for specifying power consumption and heat release of its devices (as set forth in ASHRAE Publication Thermal Guidelines for Data Processing Environments, Chapter 5, published in 2004), then these small energy conversion differences may have been accounted for, and the heat release numbers given for the configuration employed should certainly be used. However, even with this more accurate information, the total heat loads you compute must still be considered "estimates," and should be qualified as such. There are two reasons: First, your actual configuration is probably slightly different than the closest thing the manufacturer provides in the power and heat data; and second, these figures are all taken at specific line voltages, which are probably slightly different in your facility. Since actual current varies inversely with voltage, power efficiencies and, therefore, heat release characteristics, will also change slightly. None of these variations, however, are likely to be large enough to make any difference in room designs or total load requirements. The entire process of air conditioning and creating air movement is so much less exact than the differentials we are discussing as to make them meaningless outside of the laboratory.

In short, unless you have accurate manufacturer's data on heat release, you are best using total conversion of actual power consumption to heat. Obtaining reasonably accurate numbers for actual power consumption is difficult enough without becoming further concerned about minute differences in energy conversion.

Regarding the 1.08 factor in the denominator of the equation:

CFM = BTU / 1.08 x TD

The value 1.08 is a weight of air correction factor. It comes from the specific heat of air (0.24), and the volume of one pound of air under standard conditions (13.34 cu ft). Air conditioning effectiveness actually depends on the weight of air, but since calculations are done in cubic feet per minute (CFM), a conversion is necessary:

60 Minutes / 13.34 cu ft per Pound = 4.5 Pounds of Air Per Hour.

4.5 Pounds of Air Per Hour x 0.24 (Specific Heat) = 1.08

Obviously, at higher altitudes, where the air is less dense, and "standard conditions" no longer prevail, this correction factor must be further corrected for accurate calculations on large systems. For most situations in data centers, however, the 1.08 factor is just fine and, in many cases, can even be ignored without real consequence.

• Read the original article on data center cooling: Cooling blade servers.
• This was last published in September 2005

#### Have a question for an expert?

Get answers from a TechTarget expert on whatever's puzzling you.

You will be able to add details on the next page.

#### Start the conversation

Send me notifications when other members comment.

## SearchWindowsServer

• ### Thorough Exchange Server testing regimen eliminates doubt

Don't assume your Exchange 2016 implementation will work because you bought the right gear. Follow these pointers to execute a ...

• ### Organize Active Directory with these strategies

Administrators tasked with cleaning up the Active Directory user group structure need not search any further. Use these tips to ...

• ### Adobe zero-day fix precedes June Patch Tuesday

Adobe closed a zero-day vulnerability last week, which Microsoft added to its June Patch Tuesday updates. Administrators have a ...

## SearchServerVirtualization

• ### KVM troubleshooting in six simple steps

To troubleshoot common KVM issues, start by checking the logs. Then, isolate the issue and check the VM status using virsh ...

• ### Manage Switch Embedded Teaming in Windows Server 2016 Hyper-V

You can create and manage a Switch Embedded Team in Hyper-V using just a few PowerShell commands, but there are specific ...

• ### Use Sysprep to generalize Hyper-V VMs for rapid deployment

Microsoft's Sysprep tool enables rapid Hyper-V VM configuration and deployment through image generalization. Use commands to ...

## SearchCloudComputing

• ### Map hybrid cloud applications to your VPN address spaces

Enterprise networks can easily become your Achilles' heel in hybrid cloud. Follow this advice to effectively manage your VPN, as ...

• ### Evaluate PaaS vendors based on these two types of features

To determine whether a PaaS provider will meet their needs, buyers should look closely at what the vendor offers for development ...

• ### Google adds single-tenant VMs for compliance, license cares

Google continues its quest to be a more enterprise-friendly cloud, as it adds VMs with isolated hardware that could help ...

Close