Problem solve Get help with specific problems with your technologies, process and projects.

# Measuring server energy efficiency

## Increasing power densities and soaring energy costs make measuring the energy efficiency of servers more important than ever. Obtaining these metrics requires the proper tools and methods to achieve accurate results.

Increasing power densities and soaring energy costs make measuring the energy efficiency of servers more important...

than ever. Obtaining these metrics requires the proper tools and methods to achieve accurate results.

Many people attempt to measure power using an amp meter. There are two problems with this approach.

 More on this topic: Vendors near agreement for server efficiency standards Vendors tussle over measuring server efficiency

First, power is measured in watts not amps. Watts = amps x volts x power factor. Attempting to use an amp meter to measure power forces to you guess at the voltage and power factor of the circuit creating the potential for considerable error.

The second problem is both amps and watts are instantaneous measurements. Even an accurate power measurement still only tells you about a servers "performance" at that particular moment.

To accurately measure a server's efficiency while running benchmark tests you need to measure the cumulative power consumption over the entire test. Cumulative power consumption over time is an energy metric measured in watt-hours. For this you need an electric watt-hour meter. Watt-hour meters are designed to continuously monitor the amperage, voltage and power factor of a circuit to accurately determine the true energy usage. Once you have energy measurements for various servers running the same benchmark tests you have way to compare the workload achieved for the amount of energy consumed.

There are a few important things to consider when choosing an appropriate watt-hour meter. One is the resolution of the meter. Many watt-hour meters are intended to monitor large loads over long periods of time and accumulate their readings in kWh (kilowatt-hours). This means the accumulator only increments each time there is 1,000 watt-hours of energy usage. Attempting to use such a low-resolution meter on smaller circuits over short periods is like using a calendar to measure a 100-yard dash. A high-resolution meter that measures in watt-hour resolution or better is needed for this type of application.

Watt-hour meters come in many form factors. Some meters can simply be plugged inline between the load and source using standard plugs and receptacles. Other meters require you tap into the circuit to obtain the voltage measurements and clamp a current transformer around a conductor of the circuit to obtain the amperage measurements. There are also branch circuit watt-hour metering systems available that can measure the energy usage of each individual circuit within a power distribution unit.

A functional consideration is that some watt-hour meters provide network connectivity for automated reading while others require reading them visually from a digital display. A big advantage of meters with network connectivity is you can easily log a series of readings for trending and analysis.

Power and energy measurements are important metrics for data center operators today. In addition to determining equipment efficiency these metrics also indicate heat loads to assist with cooling management. Energy measurements can also be used to allocate energy costs to those responsible for their consumption creating an ongoing incentive to deploy energy efficient equipment.

About the author:Diesso has been involved in the development and deployment of automated metering solutions for over 10 years and is the founder of Smart Works, Inc which provides power and environmental metering solutions to data centers.

This was last published in May 2006

## Content

Find more PRO+ content and other member only offers, here.

#### Start the conversation

Send me notifications when other members comment.

## SearchWindowsServer

• ### Options for server management tools expand to meet IT needs

Not only do admins have to contend with a mix of server OSes, there are diverse scenarios to complicate their management. Learn ...

• ### CPU bugs add to IT stress as February Patch Tuesday drops

Administrators who rushed out fixes in January for the Meltdown and Spectre flaws then had to unwind some of those corrections ...

• ### Roll your own Windows patching tool with PowerShell

This tutorial based on PowerShell helps administrators build an automated routine that audits Windows machines, then applies ...

## SearchServerVirtualization

• ### Taking charge of VM allocation, troubleshooting methods

Long-term virtual infrastructure health leads to business growth. To achieve this, you must master virtual machine capacity ...

• ### Hype for future of container development gets dose of reality

Realistic timelines have replaced the big promises of container disruption. Virtualization administrators should expect security ...

• ### Meet these SCVMM 2016 requirements before upgrading

Before upgrading to SCVMM 2016, ensure that you meet its hardware requirements, including SCVMM 2012 R2 and Update Rollup 9 or ...

## SearchCloudComputing

• ### How to blend the advantages of cloud computing with containers

Containers and cloud sound like a perfect match. But how well does containerization help boost application portability? And will ...

• ### Containerized applications and the portability dream

To make containers work within a cloud strategy, you're going to need to carefully consider the complexities of porting an ...

• ### VMware acquisition continues move toward cloud security

VMware cloud security tools will get a boost from the company's acquisition of CloudCoreo, a security and management startup ...

Close