Data center metrics and standards guide
A comprehensive collection of articles, videos and more, hand-picked by our editors
A data center isn't a meat locker, though many are cooled so much you'd expect to see Rocky in there punching a...
By submitting your email address, you agree to receive emails regarding relevant topic offers from TechTarget and its partners. You can withdraw your consent at any time. Contact TechTarget at 275 Grove Street, Newton, MA.
side of beef.
The concept of elevated operating temperatures is simple: The computer room air conditioner system doesn't need to run as long or work as hard; cooling uses less energy and therefore costs the company less money.
You don't need to run the data center at a warmer temperature, but you do need to ask, "How warm is cool enough?"
What is a safe server temperature at the air inlet? What about safe temps for other data center equipment?
These questions have been the subject of enormous debate and consternation over the years. At some point, the inlet air entering the server becomes too hot to effectively carry away the excess heat from central processing unit, memory modules, power supplies and other devices (such as graphics processing units), resulting in system overheating and premature failures.
The exact temperature where this happens varies dramatically. The actual effectiveness of airflow cooling depends on a suitable design of the server's heat sinks, fan selection, component placement and overall airflow patterns through the system.
The American Society of Heating, Refrigerating and Air Conditioning Engineers (ASHRAE) conducts extensive research into data center cooling, yielding an ever-evolving set of recommendations through Technical Committee 9.9. The 2011 version of ASHRAE recommendations defines four classes of data center equipment (A1 through A4), each with higher allowable levels of temperature and humidity.
Class A1 systems allow temperatures from 50 degrees to 90 degrees Fahrenheit (15 degrees to 32 degrees Celsius), while Class A2 systems allow 50 degrees to 95 degrees F (10 degrees to 35 degrees C). Both systems support 20% to 80% relative humidity (RH).
ASHRAE recommendations also define two extended classes of equipment: Class A3 devices support 41 degrees to 104 degrees F (5 degrees to 40 degrees C) at 8% to 85% RH, and Class A4 systems support 41 degrees to 113 degrees F (5 degrees to 45 degrees C) at 8% to 90% RH.
The trick for determining the maximum server temperature for your data center is to understand the maximum allowable inlet temperature for the equipment used. Determine the class of each server, storage array or other device.
Most current server designs accommodate Class A1 or A2 temperature ranges, but extended temperatures into Class A3 or A4 ranges require careful attention to system design and support. Legacy systems won't survive long in a Class A3 or A4 environment, and it can take several technology refresh cycles before a data center can safely adopt the highest temperature ranges. It's best to approach elevated temperatures in gradual phases and verify system integrity at each temperature goal.
Current technologies allow IT teams to perform a broad range of management and monitoring operations remotely, but people need to get into the data center for hands-on work, and extreme temperature ranges and humidity levels can be hazardous to human health. Careful system containment approaches mitigate human exposure to higher heat.
Related Q&A from Stephen J. Bigelow
Long-distance vMotion eliminates practical geographical limitations by raising the round-trip latency limit.continue reading
Expert Steve Bigelow explains how instant clone technology helps VMware's vSphere Integrated Containers supply a baseline Linux OS and, as a result, ...continue reading
In order to ensure successful App-V deployment and get the most out of application virtualization, users should study up on App-V’s server and ...continue reading
Have a question for an expert?
Please add a title for your question
Get answers from a TechTarget expert on whatever's puzzling you.