The cable must be properly supported. If you plan on moving to 10G, beware of using high density terminations on...
By submitting your personal information, you agree that TechTarget and its partners may contact you regarding relevant content, products and special offers.
category 6 UTP systems, as you will probably only be able to energize every other port to 10G, which means you will have to reallocate some space. Also category 5e is NOT supported at all. Wire ties should not be used for bundling, but rather Velcro ties. Keep your bundles loose and not too tight. Your rack manufacturer should be able to help, too. For instance, we train people and have guidelines that incorporate all the standards.
TIA-942 also states that direct connections should only be used if required by the manufacturer. Basically point-to-point runs are just long patch cords -- you should be on a structured cabling system to not only make move adds and changes easy, but also to protect your asset investments. What I mean here is that if you have a 48-port switch (blade or otherwise), it is very hard to do direct connections without running cables all over the place. If you run everything to a central cross connect, patch cords are all that is needed to make a change. It also means that you can have several servers on several rows sharing those 48 ports so that none are wasted.
For other standards, check TIA-568-B, ISO 11801 for cabling specifics (make sure to get the latest and appropriate addendums), TIA-569 for pathways and spaces and J-STD-607 for grounding and bonding (if you don't need this for your cable, you do for your ladder rack, chassis grounds, etc.).
Dig Deeper on SDN and other network strategies
Have a question for an expert?
Please add a title for your question
Get answers from a TechTarget expert on whatever's puzzling you.