Dust contamination around servers is a growing concern as component densities and heat generation increase, and...
By submitting your personal information, you agree that TechTarget and its partners may contact you regarding relevant content, products and special offers.
air flow becomes more complex and critical. Dust buildup on filters and heat sinks can cause overheating.
Air ionization reduces the potential for static discharge and captures very fine dust particles from the air, but installation isn't generally useful or a justifiable data center expense.
The technology used to ionize air has been the subject of debate and development over the years. It's a lot more complicated than plunking an ionizer down in the server racks.
Portable "home model" air ionizers are questionable for performance, and their high air flows make these designs incompatible with equipment maintenance in data centers. Air flow control and ionization balance are critical to making air ionizers work in clean rooms -- a level of control that is unachievable in most data centers.
Avoid dust-related issues instead with good operating and maintenance procedures. Clean heat sinks and filters when servicing IT systems, and wear a grounded wrist strap when working inside servers and other equipment at the chip level. Even the best air ionization system will not add a modicum of protection against human errors.
Positive air pressure also keeps outside dust from entering the data center facility. Keep foot wipes at each door, change filters on computer room air conditioners often to avoid clogging, clean equipment filters with HEPA-filtered vacuums, and use a professional data center cleaning service once a year. These practices are all more important than air ionization.
About the author:
Robert McFarlane is a principal in charge of data center design at Shen Milsom and Wilke LLC, with more than 35 years of experience. An expert in data center power and cooling, he helped pioneer building cable design and is a corresponding member of ASHRAE TC9.9. McFarlane also teaches at Marist College's Institute for Data Center Professionals.
Dig Deeper on Data center design and facilities
Related Q&A from Robert McFarlane
Our latest firewall/VPN firmware upgrade left CPU usage at 100%. A malfunctioning DHCP-Server means people aren't getting IPs. I have to pull the ...continue reading
Do battery cooling cabinets save money over cooling batteries within the whole data center?continue reading
We're setting up a 3,700-square-foot server area with 175 server racks and in-row cooling. It's a greenfield project. How do we estimate power ...continue reading
Have a question for an expert?
Please add a title for your question
Get answers from a TechTarget expert on whatever's puzzling you.