After reading your article on "Cooling high-density racks", posed on 03 August 2005, it seems to me that a configuration...
By submitting your personal information, you agree that TechTarget and its partners may contact you regarding relevant content, products and special offers.
requiring that "hot aisle/cold aisle" rack arrangements in relative positioning to the air units keep the data center floor from being truly redundant. That is to say, if one of the air units failed, the return air from the hot aisle would not be properly cooled for re-use.
Very good question and observation. As each data center layout is a little different, it is recommended with the Hot Aisle/Cold Aisle rack arrangement to put the CRAC air units at both ends of the hot aisle. There are two situations to consider:
a) If the maximum heat load is less than the cooling load of all the CRAC units at the end of the Hot Aisles, then alternate CRAC units will and can act as the redundant cooling unit. Obviously, the airflow for each row may not be consistent. As will be noted in b) below, the use of a common plenum can help eliminate mixing of hot and cold air.
b) If the maximum heat load equals the cooling load of all the CRAC units at the end of the Hot Aisles, then space and location for the redundant units needs to determined. In this case, it would be recommended to add the redundant unit next to a unit at the end of a row and center the two units on the middle of the Hot Aisle (assumes the units are all 100% front access). This will then suggest that you rotate for equal wear the two units paired together so that one is available as a redundant unit. This however presents a problem in that if a unit fails and is not paired with a redundant unit, then your room balance could be off. To improve on this configuration, you could duct back to the CRAC units from either the complete Hot Aisle or from the center of the Hot Aisle using a common plenum (such as the space above a drop ceiling), to prevent the mixing of hot air across a Cold Aisle. With some supplemental cooling systems, the modules can be oriented to provide redundancy. This eliminates airflow across rows of racks and the need to be concerned with redundant CRAC units.
Dig Deeper on Data center design and facilities
Related Q&A from Steve Madara
Expert Steve Madara gives you a glimpse into the future of cooling the data center.continue reading
Cooling expert Steve Madara explains why it's good to be concerned about the heat from high-density racks in the data center, and what to do to ...continue reading
Cooling expert Steve Madara of Liebert Corporation explains how to evaluate the cost of cooling your data center, and why it's smart to plan for ...continue reading
Have a question for an expert?
Please add a title for your question
Get answers from a TechTarget expert on whatever's puzzling you.