Do you see any opportunities or have recommendations for KVM switch improvements re: the EPA report? Do you foresee any Energy Star specs for KVMs?
Also, do you see any efficiency value in "intelligent" Power Distribution Unit (PDU) power strips that can monitor and potentially control power at the outlet level?
I consider intelligent PDUs extremely valuable, and well worth the investment, if you make use of the load data they provide. This is particularly true when three-phase power is distributed all the way to cabinets because it enables you to achieve phase balance on each circuit while you are connecting the equipment in addition to monitoring the total loads. Be sure to take advantage of the network-connected monitoring capability most of these units now offer. And to maximize energy savings, run your equipment at the highest voltage at which it is capable of operating.
I am not a great fan of remotely controlled receptacle power switching within PDUs, although I admit they can have their place. I just don't believe there is any level of security that can absolutely prevent either an unauthorized or inadvertent shutdown. (Remember, it is said that 75 percent of data center outages result from human error.) Nor do I have the level of confidence I would like in the small switching devices packed inside these PDUs, and would not want to operate them any more than necessary.
Dig Deeper on Data center energy efficiency
Have a question for an expert?
Please add a title for your question
Get answers from a TechTarget expert on whatever's puzzling you.